BACnet receiver LoRa – IP and/or MSTP
✅ Can be used in LoRa Enless proprietary mode only
No use possible in LoRaWAN mode
✅ Frequency band 868 MHz (for use mainly in EUROPE)
✅ 118 x 79 x 43mm
✅ IP / MSTP – DHCP / BBMD interfaces
✅ BACnet ASC profile
✅ Can manage up to 40 transmitters
✅ External power supply (7.5 to 24V)
Reference of the LoRa BACnet receiver
RX BACNET 500-312
Applications of the LoRa BACnet receiver
The Enless Wireless LoRa receiver is compatible with the BACnet protocol – the reference protocol for building automation and control.
The Enless BACnet receiver complies with the specification of the B-ASC profile. It can be used both in IP and/or MSTP. DHCP as well as BBMD options can also be enabled.
The Enless BACnet receiver can collect data from as many as 40 Enless LoRa transmitters.
The BACnet LoRa receiver has two user modes:
- Object Mode: All the BACnet objects contained in the receiver are visible during discover
- Device Mode: Only those sensor BACnet objects selected to be visible for the receiver are visible during discover
The receiver is configured using an extremely easy to access and use IP server.
The BACnet receiver has an external power supply of 7.5 to 24V.
This product is LoRa Enless compatible (not LoRaWAN). It allows you to build a private proprietary Enless Wireless LoRa network. LoRaWAN transmitters from other manufacturers will not be recognised by this receiver.
|Communication mode compatibility||LoRa Enless proprietary mode.
N.B. : The use is NOT possible in mode LoRaWAN
|Frequency band||868 MHz (for use mainly in EUROPE)|
|Dimensions||L 118 x H 79 x W 43mm|
|Enclosure and IP rating||Material: ABS IP 60|
|Interfaces||IP BACnet in UDP
MSTP BACnet with BBMD
IP BACnet in UDP and MSTP BACnet
|Received Signal Strength Indicator (RSSI)||Viewable using the embedded web server and in the BACnet Object Analogue Values|
|Power supply||Main 7.5 up to 24 VDC or external 12 VDC power supply|
|LEDs||5 LEDs and 1 external power LED|
Related products :