Modbus receiver LoRa – IP and RTU RS485 / RS232 interfaces
✅ Can be used in LoRa Enless proprietary mode only
No use possible in LoRaWAN mode
✅ Frequency band 868 MHz (for use mainly in EUROPE)
✅ IP and RTU RS485 / RS232 Modbus
✅ Can handle up to 40 transmitters
✅ Compatible with Modbus PLCs
✅ Power supply 7.5 – 24 V
✅ Quick and easy to install
✅ Compact design
Reference of the LoRa Modbus receiver
RX MODBUS 500-302
Applications of the LoRa Modbus receiver
This Enless Wireless LoRa receiver is compatible with PLCs with an RS485 or an RS232 Modbus RTU interface. The receiver also manages Modbus over IP communication.
The Modbus receiver is used to collect data from our LoRa transmitters (Enless sensors only).
The LoRa Modbus receiver can handle up to 40 transmitters.
The transmitter information is stored in the receiver Modbus table. The PLC can then read the registers of the receiver to retrieve the data. It is also possible to write to the Modbus table of the receiver to re-configure already installed transmitters and add new ones.
The receiver is powered externally (either directly via the PLC power supply or via a power supply unit).
This product is LoRa compatible (not LoRaWAN). It allows you to build a radio private LoRa Enless Wireless mode.
|Communication mode compatibility||LoRa Enless proprietary mode.
N.B. : The use is NOT possible in mode LoRaWAN.
|Frequency band||868 MHz (for use mainly in EUROPE)|
|Dimensions||L 118 x H 79 x W 43 mm|
|Enclosure and IP rating||ABS IP 60|
|Interface||RS232/RS485 Modbus RTU and Modbus over IP interfaces (configuration via embedded web server)|
|RSSI signal||Accessible via embedded web server|
|Power supply||Main 7.5 up to 24 VDC or external 12 VDC power supply|
|LEDs||5 LEDs and 1 external power LED|
Related products :